Question about Goodman CKL60AR60 Air Conditioner
Could be a restriction in the meter device located near the compressor in the outdoor unit. This would be why ice was seen during the cooling season in the outdoor unit. A restriction can cause eratic pressure drops to the low side that would create a low refrigerant senario. Which creates a high pressure senario in the condenser coils and at the same time freezes at the meter device as it trys to flash from liquid to vapor.
Posted on Aug 22, 2010
If the fan motor on the outside unit is still coming on and the blower motor on the inside unit is still working properly, and your return air is not restricted (sometimes just a dirty filter), then your problem would be the charge in the unit. If over or under charged, the unit will freeze up, not just outside, but inside too. Have someone charge the unit with refrigerant and you should be okay. If any of the other problems exist, it will have to be looked into more. Hope this points you in the right direction. Good Luck!
Posted on Jul 11, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Clicking sound is the contactor engaging to start the outside unit. Check for a burnt off wire at the contactor. For some reason you are not getting power to the outside unit. If you find a burnt off wire shut off all power to it then remake the connection at the point of the circuit break.
Posted on Jun 27, 2008
are you speaking of the outside fan or inside? compressor should be a little warm but not boiling hot. the unit could be low on freon. if low it will run a while but the compressor will overheat and shut off leaving the fan running by itself ouside. if nothing outside is running check power. if you have power check the contacted outside to make sure it's pulled in. contacters are bad about going out on goodman untis. Also ants can get under contacts.
Posted on Jun 18, 2009
Tips for a great answer:
Apr 09, 2014 | Heating & Cooling
Nov 11, 2013 | Goodman Manufacturing Goodman ARUF486016...
May 31, 2012 | Goodmans Heating & Cooling
May 04, 2012 | Heating & Cooling
Mar 09, 2011 | Goodman Heating & Cooling
Oct 06, 2009 | Goodman GMS90703BXA Heater
Dec 03, 2008 | Goodman CLJ30AR32 Air Conditioner
333 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: