Question about Soleus Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: The Plug on my Soleus
This mean the compressor is drawing too much amps, caused by the back cois are clogging up and not getting rid of enough heat.Hope you clean it soon before it ruin the compressor. Thank-you-very-much!
Posted on Aug 26, 2008
All of the kfr series have a indoor coil sensor that monitors the tube temperature. In the heating mode it will sense for high temp and cut off the outdoor fan to try to lower the indoor coil temp. The cut off temp is 129f, when the coil cools down the fan will cut in and start developing heat again. If the coil continues to get warmer it will shut off completely. The system is either overcharged or the coils and or filters are dirty. All Soleus units need both lines insulated seperately and not together because the metering device is in the outdoor unit. Have your tech calibrate the charge and make sure you clean your filters every 3 months. Removing the sensor will cause the indoor coil to get too hot and possibley start to melt your housing. For further technical questions pleas call 626-378-1518 for technical questions,,professionals only.
Soleus Tech Support
Posted on Mar 13, 2009
first of all an amp reading needs to be taken to see how many amps the AC is drawing. It may be too much for the breaker. Also see what else may be wired in on the same circuit, there may be additional load on the breaker. If all amp readings are below the rating for the breaker then you may have a faulty breaker, but that's pretty unlikely. The most probable cause is you are overloading the circuit.
Posted on Sep 22, 2009
Tips for a great answer:
Jul 31, 2017 | Dehumidifiers
Jul 21, 2017 | Soleusair Heating & Cooling
Aug 08, 2016 | Soleus Heating & Cooling
Sep 16, 2014 | Soleus Heating & Cooling
Aug 10, 2013 | Soleus Ductless Mini Split 18000 Air...
Mar 05, 2013 | Soleus KFR-12G Air Conditioner
Sep 30, 2012 | Soleus SG-WAC-08ESE-C 8000 BTU Window Air...
Jul 06, 2010 | Soleus PH310R03DB Portable Air Conditioner
82 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: