Question about Siemens 100 Amp Main Breaker Renovation Panel
It depends on the type of panel. Hook the breaker to the hooks that run along the out side of the bus area, then If it's a stab lock panel just snap the breaker down into place. If it's a bolt on panel once you have pushed the breaker down into place you'll need to start and tighten the screws that connect it to the bus, at your experience level DO NOT try to connect the breaker with the power on. Once the breaker is in place connect one of the hot wires to each of the breakers lugs. If you have a Neutral (white) connect it to the Neutal bus first. If this is a sub panel with a separate ground bus you'll need to connect the gound there.
If your hooking up a motor and it runs backwards just reverse two of the hot leads.
Posted on Jul 07, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 01, 2016 | Electric Electrical Supplies
Mar 17, 2015 | Electrical Supplies
Aug 25, 2014 | Welding Tools
Jan 01, 2014 | Thomas & Betts Electrical Supplies
Sep 05, 2013 | Hardware & Accessories
Sep 07, 2011 | Heating & Cooling
Jul 20, 2011 | Siemens 100 Amp Main Breaker Renovation...
Feb 15, 2011 | Amana Hammering
Aug 19, 2009 | Heating & Cooling
Jul 28, 2008 | Motorola 3-Wire Surveillance Headset...
Aug 11, 2013 | Siemens 100 Amp Main Breaker Renovation...
124 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: