Question about Goodman CPLT24-1 13 Air Conditioner
R22 but it does not use it it is circulated in a closed loop, if the fan outside is running you may have to pull the brown wire at the split capacitor to see if the compressor is running. Also it is really important that the filters are changed and that the outdoor is clean allowing air to pass through. Turn off power before pulling the brown wire then reapply power for just a second listening for the compressor. If you hear it, turn off power, reconnect fan brown wire. Turn on power and feel if large line is cold to the touch like a good soda can should be around 45 to 55 degrees f. If not cold it need 3 to 4 pounds if the compressor is working which would indicate a leak.
Posted on Jul 06, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 27, 2014 | Heating & Cooling
Oct 19, 2013 | Goodman GPC1342H21A Air Conditioner
May 06, 2017 | Goodman Heating & Cooling
Jun 10, 2010 | 1998 Dodge Ram 1500 4WD
May 16, 2010 | Heating & Cooling
Jun 21, 2009 | Goodman Heating & Cooling
Jun 14, 2009 | Goodman CLQ36AR49 Air Conditioner
May 06, 2009 | Goodman Heating & Cooling
Oct 18, 2008 | Goodman Heating & Cooling
117 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: