Question about Heating & Cooling
Posted by Anonymous on
The capacitor aids a unit in starting and then in running.
the contactor is a switch that tells the compressor when to come on. It is usually controlled by another voltage. So the low voltage control circuit powers a coil in the contactor, which in turn, energizes the contactor, thus closing the contacts to turn on the compressor.
Posted on Jul 06, 2010
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 18, 2011 | Dometic Rooftop RV Air Conditioner
on Jan 24, 2010 | Heating & Cooling
Jun 24, 2011 | Heating & Cooling
Jun 22, 2011 | Coleman Heating & Cooling
May 22, 2010 | Goodman CKL24AR24 Air Conditioner
Mar 13, 2010 | Amana 22.6 cu. ft. Side-By-Side...
Aug 09, 2009 | Bryant Heating & Cooling
Jul 17, 2009 | Dometic Rooftop RV Air Conditioner
Jun 12, 2009 | Heating & Cooling
Apr 12, 2009 | Heating & Cooling
Apr 26, 2018 | Heating & Cooling
43 people viewed this question
Usually answered in minutes!