Question about Ruud Central System Air Conditioner
I have a 2.5 ton unit (Ruud) and the house is warm and the fan on the the unit (outside) is still running. Hard part is I am out of town, wife and family home in the hot house so it's hard to get information. Tried setting the thermostat low, switching of fan, curcuit braker and so forth. No luck.
Where should I guy start?
Have them turn the outdoor unit off and wait a few minutes. When they turn it back on they should here
the fan and the compressor come on. They are to different sounds.
If they think that they have both come on, tell them to check the black insulated suction line. it should at least cold to the touch. If not it could be a freon issue.
If the line does get cold, have them checkthe filter in the house. If that is ok tell them to turn the power off
to the outside unit. Take a garden hose and wash
the outside coils on the outdoor unit,be carefull not to
smash the fins. Wash them at an angle from top to bottom.
Posted on Jul 06, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 04, 2014 | Ruud /rheem R22 /2 Ton/13 Seer Ac...
May 11, 2013 | Ruud 3 Ton Split System Heat Pump
May 23, 2010 | Ruud Matching Split Air Conditioner
May 16, 2010 | Ruud UBHC Air Conditioner
Jun 29, 2009 | Heating & Cooling
Jun 05, 2009 | Ruud UPMC036 Air Conditioner
May 11, 2009 | Ruud UBHC Air Conditioner
Oct 23, 2008 | Ruud Heating & Cooling
May 28, 2008 | Ruud Matching Split Air Conditioner
327 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: