Question about Dometic Rooftop RV Air Conditioner
You have a faulty start capacitor. The capicitor helps start the motor ... since it is not doing its job, the motor draws LOTS more power from the line popping the breaker. Have your professional RV service center service your AC.
Thanks for your interest in FixYa.com. Please remember to evaluate this response.
Posted on Jul 05, 2010
Testimonial: "I am a technical Instructor for a major import, so I know my way around HVAC. so glad to have someone who can pin point the problem I found that the motor start fuse on top of the capacitor is melted. it still has some continuity, but looks like your diagnosis will fix it."
Hi, just some food for thought, it is a run capacitor, not a start. The capacitor has a resister across it that has over heated. The first thing to check would be the capacitor, but if the compressor is drawing enough amperage to kill the generator, I would also mega ohm the compressor windings as this may also cause this problem. Some older compressors had the start capacitor, then they added a run so the start would drop out when the compressor got up to speed. Now, they did away with most all start capacitors except on refrigeration equip. They use both single and dual capacitors on a/c units. Good answer though.
A/C, Heating, and Refrigeration Contractor
Posted on Jul 10, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 22, 2014 | Carrier 3 Ton Infinity Puron A/c outside...
Aug 27, 2013 | Maytag M6X06F2A Air Conditioner
Jul 09, 2010 | Carrier 38CKC048 Air Conditioner
Jun 02, 2010 | Dometic Rooftop RV Air Conditioner
Aug 17, 2009 | LG Heat cool Window Air Conditioner
May 03, 2009 | Frigidaire FAC107P1A Wall/Window Air...
Aug 28, 2007 | Kenmore 72055 Air Conditioner
504 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: