Question about Haier CPRD12XC7 Air Conditioner
The unit is blowing cold air then tripping out, is it blowing hot air out the back? im sure you mean exhaust air as in hot air so the reason your unit is tripping out is that its overheating and the pressures in the rerigeration system are to high, so the safety trip cuts the unit off.
replace the motor
all the best
Posted on Jul 05, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
This is a single speed permanent split capacitor motor for the condenser. One of the capacitor wires shows infinite resistance to hot and netral. The motor needs to be replaced.
Posted on Mar 31, 2009
are you speaking of the outside fan or inside? compressor should be a little warm but not boiling hot. the unit could be low on freon. if low it will run a while but the compressor will overheat and shut off leaving the fan running by itself ouside. if nothing outside is running check power. if you have power check the contacted outside to make sure it's pulled in. contacters are bad about going out on goodman untis. Also ants can get under contacts.
Posted on Jun 18, 2009
SOURCE: Exhaust fan running slow
I JUST BOUGHT A 9000BTU PROTABLE AC MY QUESTION IS IF I REDUCE THE EXAUSTE FROM THE ORIGINAL 3" TO 2" WILL IT BECOME A PROBLEM WITH THE AC OR MALFUNCTION
Posted on Jul 02, 2009
SOURCE: AC Unit is not working
if you got high volt to the outdoor machine....make sure the thermostrat is in fact on.open the control box cover to the a/c.a round or oval soda pop lookin can thing should be visually noticeable.is it blown up.thecan top will be bulged.if it is the capacitor is defective.duel capacitors control phase shift for both motors...the outdoor fan and the compressor.a big black relay with the wires comming from the outdoor fuse box should be noticeable.this is the high volt contactor, is the contactor pulled in?beets the **** out of you???grab a screw driver by the insulated handle, not the metal part of the screw driver.manually push it in.did the fan start to go???if so bad contactor or no signal from t'stat to turn machine on.if not no high volt to machine(breaker tripped or failed) or fan motor seized leading to compressor O.L.
Posted on Aug 03, 2009
Tips for a great answer:
Oct 04, 2014 | Heating & Cooling
Apr 16, 2013 | Goodman Heating & Cooling
May 15, 2012 | Amcor ALTL-12000E Portable Air Conditioner
Jul 04, 2011 | Emerson Quiet Kool 10GV13 Air Conditioner
Apr 14, 2011 | Turboair TAS-12 Air Conditioner
Jul 25, 2010 | LG LS-K2430HL Heat Cool Mini Split Air...
Jun 21, 2009 | Heating & Cooling
May 31, 2009 | Maytag Portable Air Conditioner M6P09S2A
Feb 20, 2009 | EdgeStar Portable Air Conditioner Heater
Jun 13, 2008 | DeLonghi Pinguino PACL90 Portable Air...
Oct 16, 2017 | Haier CPRD12XC7 Air Conditioner
194 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: