Question about Leviton 003-1755-W Three Rocker Switches
Am doing a 'remodel'. Discovered the 2 lights in the basement (3 way switched) received their power - from a wired outlet.
Outlet has been elimenated. Installed 'Junction Box' ran the power wire, and both switch wires plus the remaining branch of existing outlets.
Have not hit upon the right combination of wires to get both 3 way switches to work. Have not triped a breaker as yet, nor lit up my eyes. I know it is not rocket science. 3 ways always give me trouble. Help!
Email address - CaptMikeG@msn.com
Well you have to make sure of three things with three way switches...where your power comes in, where your power goes out, and that your travelers are not mixed up. Lets talk about a normal three way circuit. Power comes in to your first switch. You attach your power wire to the common terminal, usually a different color than the other terminals. The other two are your travelers, if your switches work partially you probably have these mixed up. The color traveler you have on one switch terminal has to go on the exact terminal on the other switch. Also check that your neutral is not swapped with a traveler, this will cause your eyes not to light. In between switches there is most of the time three wire cable (2 travelers and a neutral---while two wire cable is used before the switches and after it going to the light). The power then goes out of the common terminal of your second switch. If all wiring is good, I would take your switches out and check them with a continuity tester to see if they are bad. Check continuity on each switch between the common and each traveler terminal.
Posted on Jul 05, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 30, 2014 | Frigidaire GLET1031 Top Load Stacked...
Aug 28, 2013 | Victory 2005 National Renovation &...
Jan 02, 2013 | Dryers
Oct 05, 2012 | Electrical Supplies
Jul 03, 2011 | Intermatic Inc. ST01C Digital In-Wall...
Jul 09, 2010 | Hunter 27185 Remote Control
Jan 09, 2010 | Lutron Claro Screwless 2 Gang Wall Plate...
Jun 19, 2009 | Water ACE SUBMERSIBLE SUMP PUMP 1/3 HP
Feb 19, 2012 | Leviton 003-1755-W Three Rocker Switches
115 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: