Question about Carrier 38CKC036 Air Conditioner
Sounds like a bad capacitor check to if defect by checking mf rating
Posted on Jul 14, 2010
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Compressor fan motor does not
you will need to see if you are receiving you voltage to the contactor, if not then there should be a breaker or fuse next to your unit outside. the fan should engage, if the contactor is pulled in then check for voltage to the fan, it should be a black and white wire on t1 and t3, if the voltage is there then the 5mfd capacitor is bad(check with meter, if you have a meter that does that) or the fan motor is bad. on the fan motor there is a diagram with the HP,RPM,Phase, and voltage. you can either get one locally or search eBay for one. Just make sure you get a capacitor with the new motor that is rated the same, most are 5mfd but some are 7.5mfd. Hope this helps Tim
Posted on Apr 23, 2011
Tips for a great answer:
Feb 11, 2017 | Heating & Cooling
May 27, 2016 | Heating & Cooling
Jan 17, 2013 | True TSSU-27-12M-B Commercial Refrigerator
Jul 11, 2011 | GE Profile PSW26P Stainless Steel Side by...
Sep 12, 2010 | Home
Apr 25, 2010 | Refrigerators
Sep 14, 2009 | GE (PSS26MSRSS) Side by Side Refrigerator
Jul 09, 2009 | Hampton Bay 46056 Callaway II Ceiling Fan
Jun 12, 2009 | Goodman CLT36AER36 Air Conditioner
May 30, 2009 | Bryant 463AAC005BA Air Conditioner
Jun 25, 2014 | Carrier 38CKC036 Air Conditioner
Jun 13, 2014 | Carrier 38CKC036 Air Conditioner
122 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: