Question about Goodman CLQ36AR49 Air Conditioner
Posted by Anonymous on
If the fan motor on the outside condensing unit is running, but the compressor is not coming on, then yes, most of the time it is just a capacitor. It could also be the compressor has a short or bad valves. If the compressor comes on in the beginning, but shuts off while the fan motor is still running, then you could have a low/high charge, and the unit trips the internal overload switch because it overheats. Hope this helps.
Posted on Jul 11, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 29, 2014 | Goodman Heating & Cooling
Sep 02, 2013 | 18,000 BTU KSIM DUCTLESS MINI SPLIT...
Dec 20, 2010 | Goodman GMS90703BXA Heater
Aug 03, 2010 | Goodman Heating & Cooling
Sep 19, 2009 | Goodman CLQ36AR49 Air Conditioner
Jan 16, 2009 | Heating & Cooling
Nov 10, 2008 | Goodman PHKJ048-1 Air Conditioner
Jun 17, 2008 | Goodman Heating & Cooling
220 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: