Question about Solar Rheem Gas Fired Pool & Spa Heater Model P-m266a-en-c
Rheem digital gas pool heater "fan" code?????
also had "cfh" code
heater worked fine yesterday, but won't work today. either wont ignite, or seems to ignite and run fine for a minute or two, the get "FAN" code and can still smell the gas
The Fan code would indicate a problem with the combustion air blower. The is a pressure switch to indicate there is sufficent combustion air, and if not then unit shuts down. Either the fan isn't running, or there is an obsturction in the fan or exhaust piping, preventing enough air flow.
cfh would be call for heat, which would be a normal display when water temp is below setpoint
See the link below for a manual. Once you open the page look on lower right side for documents, then install manual
Posted on Jul 05, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 24, 2014 | Rheem Water Heaters
May 25, 2014 | Rheem 266K to 399K BTU Swimming Pool...
Aug 18, 2013 | Rheem 266K to 399K BTU Swimming Pool...
Mar 28, 2013 | Rheem M206A 206K BTU Pool and Spa Propane...
Jan 02, 2012 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Oct 12, 2010 | Rheem 266K to 399K BTU Swimming Pool...
Jul 05, 2009 | Solar Rheem Gas Fired Pool & Spa Heater...
1,062 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: