Question about Bryant Heating & Cooling
You said the outdoor fan is not running, can you hear the compressor running? If you can hear the compressor running then start by checking the fan capacitor. If you can't hear the compressor, then check the breakers or fuses or disconnect. One of these should be located near the outside unit. If you look at the contactor you can see the contacts. When the unit is off they should not be touching, when it is on then the moveable contacts should be pulled down and touching the stationary contacts. You can get some on at the thermostat while you watch the contactor to see if it moves when they change the thermostat to call for a/c. Let me know what you find and I can give you more advice.
Posted on Jul 04, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 02, 2014 | Ruud Central System Air Conditioner
Apr 12, 2013 | Bryant 462AJC021BA Air Conditioner
Jul 22, 2011 | Bryant 463AAC005BA Air Conditioner
Jul 06, 2010 | Heating & Cooling
May 31, 2010 | Whirlwind FH-778 Air Conditioner
Aug 03, 2009 | Carrier Heating & Cooling
May 27, 2009 | Bryant 462AJC021BA Air Conditioner
Apr 27, 2009 | Bryant 462AJC021BA Air Conditioner
Jun 10, 2008 | Amana PTH123B25AJ Heat Pump Air...
May 17, 2008 | Goodman CLQ36AR49 Air Conditioner
182 people viewed this question
Usually answered in minutes!