Question about Bryant Heating & Cooling
I think you are talking about the outdoor unit so see if you can hear the compressor running. If it isn't running then set the thermostat so that the unit is not running and give the pressure time to come down.(15mins-30mins) Discharge pressure will build up if the fan isn't running and cause the compressor to shut down that's the reason for doing this. After this set the thermostat to call for a/c then see if the compressor is running. If it isn't first check your circuit breaker or disconnect or fuses. One of these should be located close to the outdoor unit. If you have power and it's not running then look at the contactor to see if it is pulled in. The contactor supplies both the fan and compressor. After that then check you capacitor. Some use a double capacitor that works the fan and the compressor. Let me know what you find
Posted on Jul 04, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 28, 2017 | Bryant Heating & Cooling
Jul 14, 2013 | Bryant Heating & Cooling
Sep 25, 2012 | Bryant Heating & Cooling
Jul 02, 2010 | Heating & Cooling
Jun 27, 2010 | Heating & Cooling
Jul 10, 2009 | Heating & Cooling
240 people viewed this question
Usually answered in minutes!