Question about Heating & Cooling
Hi, relays will also buzz causing units to loose transformers, I have seen this in the past years also. A 2-stage heat-pump stat? I would remove the front to expose the wiring terminals and pull the hot wire red, 24 volts and that should kill the buzz. If so, the circuitry is going out and you will need a new thermostat. I would, if you have a volt meter check the incoming voltage to the stat to make sure it doesn't exceed the proper voltage rated on the cover. Max would be 30 volts ac. If its over that, the transformer is putting out to much on the secondary side and should be replaced, or it will eventually take all of the low voltage controls out. Try removing the 24 volt hot wire and also if you have a friend that has a meter or you do, check the voltage coming in to the stat. Get back to me if it exceeds the rating, as this will cause the buzzing. It may just be faulty contacts in this stat also. I wish you the best, and ask that you are kind when rating me in helping you. Please keep me posted if you need my help.
A/C Heating & Refrigeration Contractor.
Posted on Jul 03, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 11, 2013 | Heating & Cooling
Jul 10, 2012 | Heating & Cooling
Dec 27, 2010 | GE Zoneline AZ25E12D3B Air Conditioner
Nov 05, 2010 | Heating & Cooling
May 08, 2010 | Heating & Cooling
Feb 11, 2010 | Heating & Cooling
Oct 29, 2009 | Heating & Cooling
Nov 25, 2007 | Honeywell CT3600 7 Day Electronic...
565 people viewed this question
Usually answered in minutes!