Question about Nor-Lake Norlake Refrigeration 4' x 6' Kold Locker Walk-In Cooler - 6' 7'' High w/Floor
THE UNIT SEEMS TO RUN FINE BUT THE EVAPORATOR FAN ISN'T RUNNING. ANY WAY TO TEST IT COULD IT NOT WORK BECAUSE OF MOTHER BOARD. UNIT ISN'T IN DEFROST, COMPRESSOR WORKING,
CODENSER FAN WORKING THANKS FOR ANY HELP
YES see if you have 12 volts dc at the evaperator motor if you do then the motor is bad if you do not then the mother board is bad and ge recomends in this case to also change the fan motor at the same time
Posted on Apr 17, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 12, 2014 | Refrigerators
Sep 20, 2011 | GE Profile 25.6 Cu. Ft. Side-by-Side...
Check out these tips...they can help you figure out what is going wrong with your refrigerator and why it is not cooling
Refrigerator not Cooling or Fridge not Cooling
How to Defrost Refrigerator Defrost Timer Problem
Water Running in refrigerator from Freezer
Refrigerator or Freezer not Cooling or Getting Cold
Dec 27, 2010 | GE GSL25JFPBS Side by Side Refrigerator
Feb 24, 2010 | GE Profile¿ Arctica® Energy...
Nov 13, 2009 | GE Refrigerators
Nov 12, 2009 | KitchenAid KSSC48QMS Side by Side...
307 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: