Question about Goodman CKL60AR60 Air Conditioner
My unit is blowing out air but it is not cool air,my fan on thr outside is hot
There can be a couple of things that could be happening...
The first and easiest thing is to check the air filter. Make sure that it is clean... clean it or replace it. Next check the air vents to make sure that they are open and giving you good air flow...
Also check to make sure that you are not icing up on the indoor coil... ice will tell you that you are low on refrigerant. You also could be low and not be icing over, but you would need to have gauges on the unit to check that.
Finally check and clean the outdoor coil...this also can give you problems if the heat is not being removed from the outdoor unit efficiently...
You may also have a unit that is sized in such a way that it hits the balance point at about 85...that means that your heat gain is equal to the capacity of the unit...I often try to size them for about that here in Northern PA. because wqhen seldom get hotter then that and the unit then is much more effective at removeing humidity at lower temperatures...
You can also check out the tips that I have wrote about Air conditioning trouble shooting and maintenance...
Posted on Jul 04, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 21, 2015 | Hampton Bay Heating & Cooling
Jun 22, 2014 | Carrier 3 Ton Infinity Puron A/c outside...
Jun 02, 2014 | Ruud Central System Air Conditioner
May 17, 2012 | 2000 Nissan Frontier
Jun 25, 2010 | Heating & Cooling
May 31, 2009 | Ruud UBHC Air Conditioner
Jul 30, 2008 | Heating & Cooling
May 26, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
185 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: