Problem with Heaters
I have a Brivis Ducted Heating MPS series and this morning woke up with ERR 50 Hi and could smell gas. What does that mean and what should I do? We had an extreme low in temp outside last night could this have something to do with it? Need ideas ASAP Kylie1 Solution
2 Found Helpful
Hi, This is what I found for you: Error code 50 Error 50 indicates the unit has locked out after 4 ignition attempts error 46. This error can be reset by using the reset button to restart the heater, but the unit will probably lockout again if the condition has not been rectified. Check List: ? Refer checklist for error 46. Error code 46 & 55 Error 46 indicates that the unit has failed to light within the specified time. Checklist: ? Check the gas supply is turned ON at the meter, and the appliance gas ****. ? Check if other gas appliances are operating such as Gas Cooker and Hot Water Service. ? Check the gas cylinders have gas, and the cylinder valve is open (LPG only). ? Check that there is gas supply to your home. Contact your gas provider to confirm this. There may be works in your area or a problem with the supply. ? The unit may require a general service. To know more about error codes, please visit the link below: http://www.climat.com.au/downloads/1224564933BrivisNetworkerSimpleInstructionsincErrorCodes1.pdf For manual, please visit the link below: http://188.8.131.52/web/BrivisInetQuest.nsf/54fb77b4318f809c4a256648001f64bb/d3f32c564c4270f24a2570070018bf64?OpenDocument
Users Who Viewed This Problem Also Viewed:
Inproper air/fuel mix, not enough air getting into burner. This is a dangerous situation, Possable causes inclide...
test thermosat for proper operation ie-broken wire-power if good jump stat and check if unit goes on if it does than...
Hello, We have Brivis Me20 gas ducted heating. It suddenly stopped working and gives error #60. Sometimes after pressing...
I had the gas supply to to my fire turned off as I do not have a manual for the above fire. Has anyone got a copy that I can give to gas engineer to allow it to get turned on again. Trident appears to no longer be in business so unable to get directly from company.