Question about Heating & Cooling
SOURCE: Need help with wiring thermostat
first do you have a heat pump unit or standard a/c? standard a/c connections at the thermostat go like this red wire to rh-rc which is the 24v power and you don't have to remove the jumper.white goes to w which is the heating wire yellow goes to y which is the cooling wire green goes to g which is the fan wire and blue goes to c which is the common wire. so if your stat has rc- rh ywgc you should be set if the wires on the furnace correspond with the same alpha designation.orange may be used if u have a heat pump unit otherwise it may just be a spare you cap off and leave behind the subplate.
Posted on May 31, 2009
Typically if you have a yellow wire in the "y" terminal blue is used as common or "c". As far as your jumper from rc to rh, that will depend upon what type of heat you have. If all of your heat and cooling come from your packaged unit outside, yes you will need the jumper. If this does not work maybe you have a bad breaker or transfomer.
Posted on Oct 14, 2007
If you have a heat pump do not put your blue wire on b. Put it on x or c. If you don't have an inline fuse you may have blown your transformer.
Posted on Dec 04, 2007
SOURCE: im changing an old honeywell
Yes, I believe that you will be fine. If the original wiring is correct then I have listed the basic wiring below. As always read the directions and make sure the wiring matches your system.
Red wire = Rh (24v power, should have an exsisting jumper to RC)
White wire = W (heat mode)
Yellow (or sometimes blue) wire = Y (A/C)
Green wire = G (Indoor Fan)
Posted on Jul 03, 2008
Tips for a great answer:
Apr 27, 2015 | Computers & Internet
Aug 30, 2014 | Honeywell RTH3100C - Digital Heat Pump...
Feb 06, 2014 | Honeywell RTH3100C - Digital Heat Pump...
Jun 13, 2013 | Honeywell RTH3100C - Digital Heat Pump...
Apr 11, 2012 | Heating & Cooling
Sep 04, 2010 | Honeywell Heating & Cooling
Dec 20, 2008 | Honeywell Electronic Programmable...
Dec 20, 2008 | Honeywell Programmable Thermostat Heater
1,343 people viewed this question
Usually answered in minutes!