Question about Goodman GPC1330H21A Air Conditioner
If you are talking about the outdoor fan then if the fan is running the compressor should also be running. First check the capacitor and make sure no wires got pulled off. Some units use a 2 pole capacitor that runs the fan and compressor. The terminals will be Com, Herm (compressor), and Fan. If no wires are pulled off then check the capacitor and make sure the surge didn't ruin it. Let me know what you find or if you are talking about the indoor fan.
Posted on Jun 06, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 12, 2018 | Goodman Heating & Cooling
Feb 05, 2014 | Goodman Manufacturing Goodman GPH1348H41...
Feb 12, 2013 | Heating & Cooling
Apr 02, 2010 | Goodman CKL36AR36 Air Conditioner
Jul 20, 2009 | Goodman CKL42AR42 Air Conditioner
Jan 06, 2009 | Heating & Cooling
Nov 19, 2008 | Heating & Cooling
Oct 21, 2008 | Goodman CLQ36AR49 Air Conditioner
Jul 21, 2018 | Heating & Cooling
101 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: