Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Air Conditioner malfunction
Hi, Sounds like you have a short in the control circuit to me. Turn off all power going to the unit. Write down or otherwise mark the wires leaving the control board going to the thermostat. Remove them from the control board. Replace the fuse. Turn power back on and see if the fan still runs. If it does, check and or replace the heat limit switch that brings the fan on during the heat cycle. It may just need adjusted. If the fuse blows, I would think that the control board is probably bad. If it doesn't blow, Remove the thermostat. Leaving all thermostat wires open check them with an Ohm meter. There should be no continuity between them. Twist all the wires together at one end and ohm them again at the other end. You should have complete continuity on all wires. If the wiring checks out, down power the unit. Double check your wire colors and rewire the control board. With all wires open at the thermostat, turn the power back on. Touch the RED wire to the YELLOW wire. The Condensing unit should come on. Touch the RED wire to the GREEN wire. The fan should come on. Touch the RED wire to the WHITE wire. The heat should come on. Down power the unit. Replace the thermostat. Test unit. If the fuse has lasted ok but blows now it is either wired wrong at the Thermostat or the thermostat is bad. I hope I have helped. NOTE: If you can not understand these instructions. Call a licensed Heating / Air conditioning company. kstfas
Posted on Sep 23, 2007
Here is some troubleshooting tips.
Also service available.
Posted on Feb 25, 2008
Have you checked the freon level in this unit? If you are low or there is a leak it could be the problem. Hope this helps.
Posted on Dec 11, 2008
567C024RCU In this model number is the # 24. That stands for 24,000 btu's. This is a two (2) ton unit. Has this two ton unit cooled ok in the past? if so replace with the same size. But make sure yo change the indoor coil to match the size "and" efficiancy of the ew unit.
Posted on Apr 14, 2009
Tips for a great answer:
Oct 20, 2016 | Carrier Heating & Cooling
Sep 12, 2013 | Whirlpool Window Air Conditioner
Aug 04, 2011 | Heating & Cooling
Jul 26, 2011 | Carrier 38CKC036 Air Conditioner
Mar 23, 2011 | Carrier YCB243D Air Conditioner
May 19, 2010 | Carrier 38CKC036 Air Conditioner
Apr 14, 2009 | Carrier 38CKC042 Air Conditioner
Mar 19, 2008 | Carrier BCA101R Air Conditioner
61 people viewed this question
Usually answered in minutes!