Question about Teledyne Laars Laars Lite 2 Pool Heater 125,000 Btu / Propane Gas
First, check the gas valve and make sure the valve in all the way to "on" not "pilot".After shutting to off for the winter, and not turning the valve all the way on start up could be it. If that is ok, check/replace the pilot generator next to the pilot lite. One question. Does the pilot go out soon after calling for heat? Next, if you have it on "spa" or "pool" on the temperature adjusting module, try the other setting. eg. If it is on "pool", switch the knob to "spa" and adjust the temperature.
Posted on Jun 06, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Make sure thermostat is set higher than water temperature. Make sure pump is running and water is flowing through unit. If gas valve is not opening then flame sensor or gas valve is bad.
Posted on Jun 02, 2009
Tips for a great answer:
Dec 28, 2015 | Bosch & Tankless LP Hot Water Heater
May 26, 2014 | Hayward Pool & Spa
Dec 23, 2010 | Procom ML300EBC Heater
Jul 11, 2010 | Water Heaters
Sep 05, 2009 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Aug 10, 2009 | Water Heaters
Mar 29, 2009 | Desa International GWN10T Wall Mounted...
Mar 02, 2009 | Dyna Glo "" Natural Gas Heater Mn200tba
Nov 24, 2008 | Clairion Convection Heater - HC-1500
Sep 14, 2017 | Heating & Cooling
Jun 26, 2011 | Teledyne Laars Laars Lite 2 Pool Heater...
425 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: