Question about Superior Lennox Blower Thermal Sensor - BTS
This usually happens when your system isn't charged right, meaning, over or under charged, or you have a problem with the return air being restricted like the filter being to dirty. Anyways, the coil on the inside of the unit is freezing up which is causing the excess water and the low air flow. First check the filter since thats the cheapest, but it's more than likely the charge of refrigerant thats the problem. Hope this helps.
Posted on Jun 26, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 29, 2011 | Whirlpool Water Heaters
Oct 28, 2010 | York Furnace Draft Inducer Blower Fasco #...
Jun 22, 2010 | Ruud UBHC Air Conditioner
Feb 08, 2010 | Goodman CLQ36AR49 Air Conditioner
Jan 28, 2010 | Heating & Cooling
Jan 11, 2010 | Goodman Heating & Cooling
Jun 21, 2009 | Weather King 10AJA3601AH Air Conditioner
Apr 26, 2009 | Goodman CKL42AR42 Air Conditioner
Oct 01, 2008 | Goodman GDS80904BNA Open Flame Heater
Nov 08, 2014 | Superior Lennox Blower Thermal Sensor -...
135 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: