Question about Coleman Heating & Cooling
Using the model number and serial number for the furnace, you should be able to order a new wire harness for the the air handler. Most wire harnesses are comprised of the wires themselves with a polarized molex connector at either side that plug into the various locations within the air handler.
Couple that with the original wiring diagram with the unit and you should be able to do the wiring yourself. But without a model and serial number of the unit, you may be a little in over your head.
Remember that the key is not to just rewire the furnace and install a new motor but rather to find the root cause to the failure. I would suggest checking the sequencer or fan relay. A stuck relay or failed relay may have allowed the blower to run without the proper voltage and caused the failure in the first place.
Simply replacing parts without test the whole unit may yield another short term fix and quick failure.
Posted on Jun 06, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 01, 2014 | Goodman Heating & Cooling
Apr 04, 2011 | Honeywell Heating & Cooling
Aug 10, 2010 | Heating & Cooling
Aug 05, 2010 | Honeywell Heating & Cooling
Aug 01, 2010 | Goodman CKL42AR42 Air Conditioner
Jun 30, 2010 | Carrier 38CKC042 Air Conditioner
Aug 06, 2009 | Comfort-Aire HMC36AT-1 Air Conditioner
Jun 06, 2009 | Goodman CLQ36AR49 Air Conditioner
102 people viewed this question
Usually answered in minutes!