Question about Frigidaire FAA065M7A Air Conditioner
My ac unit wont start up. i have checked the wiring it is ok. the unit powers up on the display but wont even run the fan
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
How do you know power is at the outdoor unit? Did you check it with a meter? Check your breaker. If there's power at the outdoor unit, then shut the power and test your contacter. If the contacter has supply power then check the low voltage (24-28 volts) that operates the contacter, and if none check the low pressure cut-out,high pressure cut-out and make sure the thermostat is calling for cool. All ok so far, then test your capacitor. I forgot to mention to check for loose, broken, and disconnected wires.
Aug 24, 2013 | Carrier Heating & Cooling
Jun 22, 2012 | Carrier Heating & Cooling
Jun 18, 2011 | HP Compaq Presario 2200 Notebook
Aug 21, 2010 | Gateway LT2030u Netbook
May 25, 2010 | Exercise & Fitness
Aug 15, 2009 | Dryers
Mar 08, 2009 | 1991 Chevrolet Silverado 2500
Jun 26, 2008 | Goodman CKL60AR60 Air Conditioner
Jun 23, 2008 | Carrier Heating & Cooling
529 people viewed this question
Usually answered in minutes!