Question about Goodman CLQ36AR49 Air Conditioner
My air conditioner doen't start
Check to make sure that the power is on to the outdoor unit and the furnce. Check breakers and fuses. There may also be a disconnect outside located by the condenser. It is probably a gray box, loft the cover and make sure the shitch is on. Otherwise if you turn the thermostat to cool, if the furnace blower comes on and the outdoor unit does not check the following. Turn off poer to outdoor condenser and open up the electrical compartment on the condensing unit outside. There is a round or oval cylinder inside. Its probably silver in color. That is the capacitor. If the top is bulged, its a true sign of a capacitor failure. Take the capacitor out and take it to your local HVAC Wholesaler of contractor. The part should cost you around 15 to 25 dollars. If this does not work, let me know.
Posted on Jun 05, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 30, 2014 | Goodman Manufacturing Goodman MSG18HWN1W...
Oct 06, 2010 | Goodman CLQ36AR49 Air Conditioner
Aug 06, 2010 | Goodman CKL36AR36 Air Conditioner
Jul 17, 2010 | Goodman CLQ36AR49 Air Conditioner
Jun 27, 2010 | Goodman Heating & Cooling
Jul 11, 2009 | Goodman CKL24AR24 Air Conditioner
Apr 28, 2009 | Goodman CKL60AR60 Air Conditioner
105 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: