Question about Heating & Cooling
I am going to assume you are talking about the outside condenser. If the thermostat is calling for heat and the furnace blower is on, you may want to check the capacitor inside the outside unit. Disconnect the power to the outdoor unit and open up the electrical compartment. There is either a round or oval silver cylinder inside by the contactor. That is the capacitor. If the top is buldged it is a true sign of a capacitor failure. Remove the cap and take to your local HVAC Wholsaler or contractor to have them replace it. It is a very common part and should cost you around 15 to 25 dollars. Let me know if this helps.
Posted on Jun 05, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 06, 2015 | Elite Sl 3000 Ul Sliding Gate Operator
Jan 25, 2015 | Heating & Cooling
Jul 01, 2013 | Computers & Internet
Oct 14, 2010 | Televison & Video
Aug 07, 2010 | Hardware & Accessories
Jul 22, 2009 | Epson AcuLaser C1900 Printer
May 24, 2009 | Heating & Cooling
Feb 08, 2009 | 1994 Volkswagen Jetta
Jun 18, 2008 | Kenmore 2.1 cu. ft. Portable Top Load...
22 people viewed this question
Usually answered in minutes!