Question about Pass & Seymour #690WGCC6 15A White 2SP UL Switches
Wire from the breaker goes to the LINE side with the break-off tie connecting the two screw terminals on that side (common feed). The light "HOT" and fan "HOT" wires will be connected to the LOAD side of the switch. If the neutral (white) wires are present in this box, they should be joined together (wirenut). I prefer connecting the light to the upper switch terminal and the fan to the lower switch terminal since the light is an outside light and I presume that the switch is located next to a door or entry.
Posted on Jul 18, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 26, 2017 | Dryers
Mar 23, 2016 | Dryers
Jul 14, 2014 | Hunter 25872 Sojourn II Brushed Chrome...
Oct 12, 2013 | Craftmade International CQ52 Ceiling Fan
Jun 21, 2011 | Pass & Seymour Legrand TM8111 Three Single...
Feb 20, 2011 | Hunter Ceiling Fan - 2053
Jan 18, 2011 | Hunter Ceiling Fan Control Switch
Oct 02, 2010 | Electrical Supplies
Jul 07, 2009 | Hampton Bay 46056 Callaway II Ceiling Fan
May 09, 2009 | Hunter 22890 52'' Low Profile Plus Antique...
141 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: