Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Ruud Furnace needs replacement
What part of the country?
How many square feet in the house?
Single pane glass?
Many factors should be considered by a professional.
However if the old unit worked OK, a new 80% 70,000 unit will most likeley replace a 24 year old 60-70% 75,000 unit.
Posted on Dec 16, 2008
If the blower motor runs continousley and the thermostat is not set to fan then the intergrated control board is malfunctioning and must be replaced. Usually because the relay that energized the motor is bad. If you are refering to the inducer motor running all the time then the pressure switch is open and must checked for a restriction in the flue pipe or blockage in the vent.
Posted on Jan 17, 2011
Testimonial: "Thank you so much, very helpful"
Tips for a great answer:
Mar 19, 2017 | Ruud Heating & Cooling
Dec 02, 2015 | Ruud Heating & Cooling
Mar 01, 2015 | Ruud Heating & Cooling
Sep 24, 2013 | Ruud Rheem Weather King Furnace Igniter...
Sep 29, 2012 | Ruud Heating & Cooling
Oct 02, 2011 | Ruud UBHC Air Conditioner
Feb 08, 2011 | Ruud Heating & Cooling
Jan 17, 2011 | Heating & Cooling
Dec 14, 2008 | Carrier 38CKC042 Air Conditioner
72 people viewed this question
Usually answered in minutes!