Question about Bryant 463AAC008BA Air Conditioner
Hi if the indoor fan continues to run after the unit is done cooling, you either have a fan relay located in the indoor unit that is bad or stuck, or a problem in the thermostat with the fan contacts not opening when its satisfied. Pull the cover from the thermostat to expose the wiring. Find the G/Green wire. This is the fan wire. Take a small screw driver and carefully loosen screw and take this wire off. Give it a couple of minutes to see if it shuts off. If it does shut off, the thermostat is faulty and you will need a new one. If it still runs, you will have to check the indoor unit and find the fan relay. If this system is gas fired for heat, it will have a combination fan/High limit control that is the problem, more then likely stuck. Look at the wiring diagram on the panel and it will show you the fan control. You can try tapping on it to see if you can un- stick it. If not, it will need to be replaced. If its just a fan relay, it will be black about the size of a wooded match box with around 5 wire terminals on it. If you have someone turn the stat on and you should be able to hear it click. Do the checks with the stat and let me no the out come and we can go from there.
Posted on Jun 04, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 28, 2017 | Bryant Heating & Cooling
Nov 26, 2012 | Bryant Heating & Cooling
Nov 15, 2012 | Bryant 463AAC008BA Air Conditioner
Aug 23, 2012 | Bryant 463AAC008BA Air Conditioner
Jul 21, 2010 | Bryant 463AAC008BA Air Conditioner
Jul 04, 2010 | Bryant Heating & Cooling
Jun 27, 2010 | Heating & Cooling
Nov 11, 2009 | Bryant 463AAC008BA Air Conditioner
Sep 17, 2009 | Bryant 463AAC008BA Air Conditioner
Aug 19, 2009 | Bryant 463AAC008BA Air Conditioner
401 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: