Question about Heating & Cooling
Rheem air conditionerModel# RMSU-48HWhen condensor defrost on heating mode should the indoor fan still be running or must it switch onand off as unit sicles?
The indoor fan will continue to run. When heat pump goes into defrost the outdoor fan stops, the reversing valve switches and the unit is basically working in the cooling mode. In order for you not to feel a blast of cold air in the winter the electric strip heat also comes on so the indoor fan must run while the strip heaters are on.
Posted on Jun 04, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 30, 2016 | LG Heating & Cooling
Apr 14, 2015 | Heating & Cooling
Sep 06, 2013 | Goodman PHKJ048-1 Air Conditioner
Sep 14, 2010 | DeLonghi Heating & Cooling
May 31, 2010 | Fujitsu 24R1 Air Conditioner
Apr 12, 2010 | Amana PTH123B25AJ Heat Pump Air...
Mar 02, 2010 | Heating & Cooling
Jun 18, 2008 | Heating & Cooling
May 24, 2017 | Refrigerators
Sep 25, 2017 | Heating & Cooling
196 people viewed this question
Usually answered in minutes!