Question about Heating & Cooling
Yes it is absolutely necessary to evacuate the system. But before evacuation of the system, a pressure test should be performed with compressed nitrogen to check and verify that there are no leaks within the system.
The only way to properly evacuate a system is with a vacuum pump. Most professionals prefer a dual stage pump that can evacuate quickly and then kicks into a lower gear to complete the process.
A triple evacuation is the best method, whereas the system is pulled down to 500 microns, and then the vacuum is broke with dry nitrogen. This process is repeated 3 times to complete evacuation. Once the system has been pulled below 500 microns for the third time, the system should be left in a vacuum for at least 5 minutes and verify there is no more leaks or moisture in the system. If after 5 minutes, your micron reading has not elevated, then your good to go. If it has, then you need to continue working.
The reason the system needs to be evacuated is to remove all the moisture from the system. Moisture and refrigerant do not mix and elevated moisture levels within a refrigeration system can cause severe damage to all the components including the compressor, expansion valves, filter driers, reversing valves, service valves, etc.etc... These damages could also void the warranty due to improper installation and start-up practices and procedures.
Posted on Jun 03, 2010
Please check the link bellow and go through the article to have an in-depth knowledge about your query…
let us know if you want somethin more else please accept the suggestion.
Thank You for contacting Fixya.com
Posted on Jun 03, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 14, 2013 | Whirlpool AD50USS Dehumidifier
Apr 10, 2017 | Heating & Cooling
May 22, 2012 | Heating & Cooling
Apr 01, 2011 | Heating & Cooling
Nov 06, 2010 | KitchenAid KSCS25FKSS Side by Side...
May 28, 2010 | Samsung AQ24 Air Conditioner
Jul 29, 2009 | 1999 Chevrolet Suburban
Jul 12, 2009 | Coleman Heating & Cooling
Jan 17, 2009 | Heating & Cooling
Jul 29, 2008 | Heating & Cooling
Aug 21, 2017 | Heating & Cooling
39 people viewed this question
Usually answered in minutes!