Question about Carrier 38CKC042 Air Conditioner
I have a Carrier Infinity heat pump. The dual speed fan motor went out. The dealer came and replaced the motor and it the unit did not work so they replaced the circuit board. The new fan ran backwards. They ordered another fan and replaced it and that one ran backwards. When it runs backwards there is no suction in where the filters are and the unit freezes up.
Make sure the capacitor is connected to the start lead, not the run lead(s). Also some fans come with some wires you can switch to reverse the direction. If your motor has them there will be 4 and the label on the motor will tell you how to connect them. Let me know if you need more assistance or if this helps.
Posted on Jun 03, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 17, 2012 | Goodman CLQ36AR49 Air Conditioner
Aug 21, 2010 | Carrier 38CKC036 Air Conditioner
Jul 05, 2009 | Heating & Cooling
May 31, 2009 | Carrier 52CQ-312-4 Comfort Series Heat...
May 11, 2009 | Carrier 38CKC036 Air Conditioner
Feb 27, 2009 | Carrier Heating & Cooling
Dec 07, 2008 | Carrier Heating & Cooling
Aug 14, 2008 | Carrier Heating & Cooling
Jul 01, 2008 | Heating & Cooling
Apr 20, 2008 | Carrier 38CKC036 Air Conditioner
384 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: