Question about Mastercool 67680 Evaporative Cooler Air Conditioner
There is water leaking out of the top cap of my MasterCool unit (don't know the model #), along the front of the cooler pads and out through the vent panel. The rubber strips on the underside of the top cap that rest on the pads have come off, which may be the problem. Is there a replacement part # for these? Can they be replaced with anything else?
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: New Mastercool pads smell bad
The cellulose pads in a mastercool are glued together and usually the adhesive is what you smell. It may take a while for it to go away. Strange as it may seem, as the pads get more mineralization and you use it more the smell will go away. Do not use a cooler for your whole house without plenty of exhaust through a window or an updux. Coolers work best when there is plenty of freely moving air.
Posted on May 31, 2009
If your motor only works on low speed and not on high speed first check to see if you have the proper voltage to high speed. Check with a voltmeter or multimeter, check from common on the motor to high speed on the motor at the switch. If you have the proper voltage then you have an open winding on high speed and the motor needs replaced. If you don’t have the proper voltage or any volts, then the switch is bad and needs replaced. This also will be the same if, medium speed won’t work and low speed does.
Posted on May 30, 2010
Testimonial: "great answer - I'll check it today"
SOURCE: do they make some kind
Best way is to get a sheetmetal shop inyour area to make one for you.. Give them the exact size of the opening and then tell them you want a 3/4" flange all the way around and make sure the duct connection is what you need.. Let us know if you need anything else.. please vote.
Posted on Sep 05, 2010
Is it a side draft or downdraft cooler? My instructions simply say to cover the unit, disconnect the power and drain the water for winter. They don't suggest removing or cleaning the pads until spring. If you're ductwork also is connected to your furnace, and you don't have a cookie sheet(piece of sheet metal that fits in a slot beneath mastercool unit or along the inside if it's a side draft cooler) then besides covering the entire unit you cn probably cover the blower, also called the squirrel cage, with a canvas cover.
Posted on Oct 14, 2010
Tips for a great answer:
Oct 17, 2014 | Fasco Bradford White Water Hot Heater...
Jul 21, 2011 | Mastercool 67471 Evaporative Cooler Air...
Dec 18, 2010 | Water Heaters
Oct 09, 2010 | Mastercool 67680 Evaporative Cooler Air...
Aug 26, 2010 | Maytag MMV4203D Microwave Oven
Mar 20, 2010 | Bosch Evolution 500 SHE55M06UC 24 in...
Jul 17, 2009 | Mastercool 67471 Evaporative Cooler Air...
Jul 09, 2009 | Mastercool 67471 Evaporative Cooler Air...
Jul 22, 2008 | Intertherm Heating & Cooling
May 15, 2008 | Dishwashers
49 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: