Question about Goodman CPLT24-1 13 Air Conditioner
You have a low refrigerant charge. Your low reading which coresponds to the temp at the coil 49psi is about 20 degrees fr. It should be closer to 70 psi depending on the ambient temp indoors. The coil has to be above freezing I usually shoot for 38 to 40. your sub cooling needs to be at least ten. And if you cant feel the heat leaving throuhg the condenser fan it aint moving it.
Posted on Jul 08, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 18, 2015 | Dyson AM04 Hot Cool Fan Heater White
on Dec 14, 2009 | Heating & Cooling
Jul 08, 2015 | Honeywell Electronic Programmable...
Jan 06, 2015 | Heating & Cooling
Mar 27, 2010 | Hitachi Variable Frequency Drive Inverter
Dec 17, 2009 | Pontiac Grand Am Cars & Trucks
Apr 22, 2009 | Heating & Cooling
Jun 27, 2008 | Continental Fish File Refrigerator - 1 Row
Dec 20, 2007 | Ruud UAMB Air Conditioner
102 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: