Question about Jandy Laars LX Pool Heater / 400,000 BTU / Natural Gas
I have a Jandy lx400 gas heater and it keeps shutting down showing "air flo sw" on the readout. I have checked the switch and it closes when the blower is running but the unit still fails. The company that installed the unit says it could be the fan motor or even the display board which they say costs 900 dollars. Any help?
Mine does the same. Sounds like you checked the air pressure switch, but the high temp switch and bad airflow can also cause this problem. Check the two white wires that lead to the heat sensor vent drain tube exits. Make sure the spade connectors aren't shorted. Try testing the temp sensor like you did the pressure switch to make sure the circuit is properly closing when in use (or use a temporary jumper to bypass as a test.) Check the bottom of the pan for any dust or crud that could block the airflow below or around the burners and last of my options- increase clearance around the unit to aid air flow.
Posted on Mar 06, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 29, 2015 | Jandy LAARS LX250 - NATURAL GAS, DIGITAL...
Apr 11, 2011 | Jandy Laars LX Pool Heater / 400,000 BTU /...
May 09, 2009 | Jandy LAARS LX400 - NATURAL GAS, DIGITAL...
1,045 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: