Question about Whirlpool Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: dometic roof air
Sounds like the unit either has been miswired from the beginning or there is a stuck contactor relay.
The more rare scenario is that the control wire between the t-stat and the contactor is shorting to a power source causing the relay to energize. Good Luck!
Posted on Jun 23, 2008
SOURCE: I have a coleman/evcon heat
I would check the hig voltage power supply to the unit. Check the main breaker and make sure it is on. Check the disconnect and make sure there is power at that point to the condensing unit. The contactor will kick in from the low voltage in the control circuit.
Posted on Jul 11, 2008
sounds like you have short in the low voltge side of the electrical circuit. I would check the thermostat wires outside at the condenser. look for any bare or exposed wires from where the wire comes from the house to the condenser. the thermostat wire will be a brown wire that is run on the outside which sends a signal to the contactor to make the condenser work. common cause his rodents or happens when weed whacking around condenser. Hope this get you started.
Posted on Apr 26, 2009
Tips for a great answer:
Jul 21, 2015 | Dometic Rooftop RV Air Conditioner
Oct 04, 2010 | Dometic Rooftop RV Air Conditioner
Apr 19, 2010 | Intertherm P3RA-030K Air Conditioner
Jul 30, 2009 | Whirlpool Heating & Cooling
May 21, 2009 | Whirlpool Electronic Window Air...
Feb 07, 2009 | Dometic Rooftop RV Air Conditioner
Jun 23, 2008 | Whirlpool ACQ108XL Air Conditioner
Aug 08, 2017 | Whirlpool Heating & Cooling
90 people viewed this question
Usually answered in minutes!