Question about Goodman CLQ60AR61 Air Conditioner
My unit is 3 years old. We have recently heard water leaking in the crawl space where our main vent and filter are. The unit is located directly above this. We were told to pour bleach down the pvc tube that it was probably clogged up with algae. We have done this 3 times in the past 2 days. The unit isnt cold when this is happening. We have to turn it off and hope it works for a little while. Do you have another solution
Sounds like the evap coil is freezing. it is frozen if you have low air flow. check the lines and see if your suction line is freezing. also check your filter. if you think your drain line is clogged cut the line and blow out with an air compressor or nitrogen. all you should need to fix the line would be a 3/4 in coupling or a union. hope this helps
Posted on May 31, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 27, 2013 | Kenmore Dryers
Oct 05, 2010 | Noritz 6.9 Gallon Residential Direct Vent...
Jan 08, 2010 | Ruud UBHC Air Conditioner
Nov 08, 2009 | Bosch PowerStar AE115 Tankless Water...
Jun 06, 2009 | Protech Systems FasNSeal FSWMKE4 4" Vent...
Apr 01, 2009 | Protech Systems FasNSeal FSWMKE4 4" Vent...
Dec 04, 2008 | Maytag Atlantis MDE7400AY Electric Dryer
Sep 12, 2008 | Heating & Cooling
84 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: