Question about Goodman CKL60AR60 Air Conditioner
We had a power surge and there is no power to my thermostat. I have power to the air handeler and the compressor outside. I have oppened the trane air handeler in the attic and am looking for this circuit borad and three amp fuse I have seen on the help boards but i can not find either, I have found a 25 amp fuse inside the handeler but I believe this is to the blower moter, due to the high amp rating. Can you tell me where this fuse is, Its driving me crazy tring to find it. thank you for your assistance ib advance. (The trane air handler number is TWEO36P 130BO)
Rarely is the blower motor fused that might be a 2.5 amp fuse read across the fuse if you have 24 volts it is bad.
Posted on Aug 12, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Clicking sound is the contactor engaging to start the outside unit. Check for a burnt off wire at the contactor. For some reason you are not getting power to the outside unit. If you find a burnt off wire shut off all power to it then remake the connection at the point of the circuit break.
Posted on Jun 27, 2008
SOURCE: the air handler won't shut off
As long as the t-stat fan switch is in the auto position the problem sounds like fan relay is stuck. It looks like a little black box about 2 inches square. Has 5 positions on it two of them are for 24 volts.
Be sure you turn off power before pulling it out. Make note of the arrangement of the wires maybe label as you remove them. ken
Posted on Dec 27, 2008
Look at the contactor on the condensing unit, remove the low voltage wires to the contactor and turn on the system. If the low voltage fuse doesn't blow, replace the contactor.
Posted on Jul 07, 2009
are you getting 120v at the "cool" terminal on the board try taking one of the motor leads and hooking it up to the 110v going into the control board if that works check to see if you have 24v at the "G" terminal if you have 24v at "G" and no voltage coming off of "Heat Or COOL" then i would replace the board
Posted on Jul 14, 2009
SOURCE: Goodman Air (outside unit)
was there any refrigerant loss? "bumping" that results in movng usualy causes a leak.If the system is totally empty, It shouldn't start.. If it did major oh nos! will appear. Does it not start all? and was it running when it got thumped? May have to call a tech out on it. Sorry.
Posted on Jul 29, 2009
Tips for a great answer:
May 26, 2014 | Rheem RASL024JEC-RHPNHM2421JC 2 Ton 18.50...
on Aug 22, 2013 | Heating & Cooling
Feb 09, 2014 | Fujitsu 24C1 Air Conditioner
Jun 10, 2010 | Coleman Mach 15 Air Conditioner
Jan 06, 2010 | Ruud Heating & Cooling
Oct 08, 2009 | Ruud Central System Air Conditioner
Jun 17, 2009 | Carrier 38BRC036 Air Conditioner
Jul 17, 2008 | Dometic Rooftop RV Air Conditioner
Jun 13, 2008 | Honeywell Heating & Cooling
191 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: