Question about Fujitsu 24R1 Air Conditioner
The indoor fan will not run at normal fan speed untill the indoor coil reaches 32oC. This is done so that a cold draught is not felt when outdoor unit is not running. Check to make sure the outdoor unit is operating. If the outdoor fan is running but there is no indoor fan after 5 mins then you must likely have a gas issue or a fault compressor circuit.
Posted on Aug 13, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 19, 2017 | Heating & Cooling
Jan 07, 2016 | Sanyo 24KS72 Split System Air Conditioner
Jun 19, 2014 | Goodman CKL36AR36 Air Conditioner
Jun 03, 2010 | Heating & Cooling
Oct 06, 2009 | Sanyo Heating & Cooling
May 16, 2009 | Fujitsu 24R1 Air Conditioner
Feb 01, 2009 | LG LS-K1830CL Cool Mini Split Air...
Dec 23, 2008 | Honeywell Electronic Programmable...
Oct 26, 2008 | Heating & Cooling
Hello Tom , I'm sure i can help you with this.... I work on these units everyday. unfortuneately im not there to put my hands on it but i will explain as clearly as possible. The most common problem I tend to find with these units is that the control board and indoor fan motor tends to go bad in these quite often. If you put the unit in A/C MODE and/or Fan mode and set it to high if it will not speed up from low , then your problem could be in a couple different places. 1st. The bearings in the fan motor could be wearing down , 2nd The Control board could be bad in that its not telling the fan motor to speed up.
And when you tell me that the compressor doesnt run in that mode at any given time..... which the electric heat and heat pump itself works together so that when the load is really tough that the heat pump doesnt over work and in general saves life on your compressor.
Solution is this.
Take your indoor fan motor off and and drill out the rivits and it pulls apart easy, and replace the bearings and grease them.
ALIGNMENT OF THE FAN IS A MUST. doesnt cost much at all the fix this. Just a little time and bearings
Replace the Board in the control box
This my friend will definetly solve your problem. These problems i see everyday with these same units.
Oct 10, 2007 | GE Zoneline Deluxe Series Cooling &...
294 people viewed this question
Usually answered in minutes!