Question about Mitsubishi Mr. Slim MXZ30TN Air Conditioner
It sounds like your unit has a bad start capacitor or start relay. If you have a thermostatic expansion valve a lot of times the unit pressures won't equalize for long periods of time, so the compressor needs additional starting torque. If you let the unit set long enough the pressures will equalize and the compressor will start, but if you try to restart it before it equalizes then the start capacitor and start relay add the additional starting torque, to allow the compressor to start with unequal pressures.
You probably already have them and they are bad, if not you need to have them added to your system.
Posted on Jun 01, 2010
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
155 people viewed this question
Usually answered in minutes!