Question about Heating & Cooling
Check the fuses in you disconnect easy way if you have a meter check across line top L1-L2 should have 208-230, same on load side should have same voltage. if not bad fuse. check and see when the unit starts up if the fan spins. if so fan is probably good. if the units trips as soon as you flip the breaker the compressor is probably shorted or you have a shorted wire. if it takes a good 10 seconds i wold test the capacitor in uF. if you are not good with electric or using test equipment i would recommend calling someone. hope this was some what of help to you.
Posted on May 30, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jun 06, 2013 | Dometic Rooftop RV Air Conditioner
Nov 25, 2012 | Ruud Matching Split Air Conditioner
Oct 27, 2011 | Refrigerators
Jan 03, 2010 | Dayton D-F79 Electric Space Heater- the...
Jul 15, 2009 | Blue Sea Sea 3082 Dc 10 Position Toggle...
Jul 05, 2009 | Dometic Rooftop RV Air Conditioner
Jun 05, 2008 | LG L1004R Air Conditioner
66 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: