Question about Hayward H-series Electronic Gas Pool Heater H400
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Not at all uncommon. New heaters have to glaze over the file tile in the burner chamber and will often smoke and smell during the first week or so of operation.
Using a mirror, check to see that your flames are about 4" proud of the burner tubes when running. As long as they are and the color is a nice blue with little to no yellow/orange color, the heater is fine.
Posted on Jun 14, 2009
SOURCE: Hayward H400FDN won't stay lit
It is probably not sensing flame. You either have a clogged orifice underneath the flame sensor and you probably need to have the gas pressure assessed, meter size and gas valve pressure adjustment. These heaters need 2" wc of gas pressure.
Posted on May 20, 2010
Try resetting it by turning off the breaker that supplies power to the heater. This should be located in the power box at the pool equipment. It is probably a 15 amp breaker.
Posted on Apr 18, 2011
SOURCE: Hayward H400FDN pool heater It
The Error is Sb which indicates a fault with the Keypad which requires replacing.
There are 2 options for this part.
Posted on Jul 16, 2011
Tips for a great answer:
Jan 28, 2014 | Hayward Industrial Products H400FDN...
Jan 28, 2012 | Hayward H400FDN Low NOx Natural Gas Pool...
Nov 03, 2011 | Hayward H400FDN Low NOx Natural Gas Pool...
Apr 17, 2010 | Hayward H400FDN Low NOx Natural Gas Pool...
May 28, 2009 | Hayward H Series Pool & Spa Heater 400k...
Mar 23, 2009 | Hayward H400FDN Low NOx Natural Gas Pool...
242 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: