Question about Lite On Laars Lite 2 Heaters: 250,000BTU MV Heater
It should be at 750 mv or a bit less if in the system under load, test it out ot system, make sure flame is at the tip of the pilot generator, as the temprerature differentail across its body is what creates the 3/4 volt or 750 mv. easier to simply buy one, test the valve using a AA battery with a wire taped on each end, simulate a pilot generator by attaching the wires where the generators wires went, if it works its ok, and generator is bad
Posted on May 29, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 08, 2015 | Jandy Pool & Spa
Feb 11, 2015 | Cozy Heating & Cooling
Aug 19, 2014 | Pool & Spa
Dec 12, 2013 | Water Heaters
Nov 20, 2013 | Teledyne Laars Pool & Spa
Sep 12, 2013 | Jandy Lite 2 Natural Gas Pilot Light...
Aug 17, 2013 | Teledyne Laars Laars Lite 2 Pool Heater...
Mar 17, 2011 | Jandy Lite 2 Natural Gas Pilot Light...
Dec 31, 2010 | Teledyne Laars IGNITION TRANSFORMER
Sep 04, 2010 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
739 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: