Question about Briggs & Stratton Briggs Stratton Portable Generator6250w Surge
THE GENERATOR IS A GENERAC 5000 WATT. I HAD A BAD BRUSH BLOCK AND REPLACED IT BUT NO HELP. I TOOK SOME RESISTANCE READINGS OF THE STATOR AND ROTOR WHICH ARE LISTED BELOW. ARE THESE IN SPEC??
ROTOR 26.2 OHMS
STATOR RED/BLUE .4 OHMS
STATOR BLUE/GRAY .7 OHMS
GRAY/RED .5 OHMS
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
As long as you have continuity through the stator and rotor windings, and no continuity from the windings to the core, you should be good.
If the brush block was replaced due to it being defective, take a look at the diode and capacitor regulator as well. Using a multimeter, the diode should indicate continuity in one direction, infinite resistance in the other. If you get this, then replace the capacitor. If not, then replace the diode, and likely the capacitor as well.
Posted on Jun 12, 2010
Tips for a great answer:
Jun 28, 2016 | Generac Electrical Supplies
Oct 10, 2014 | Briggs & Stratton Gas Powered 3500-4375...
May 13, 2014 | Briggs & Stratton Briggs and Stratton...
Dec 09, 2013 | Briggs & Stratton Briggs Stratton 6200...
Sep 14, 2011 | Briggs & Stratton Briggs and Stratton...
Jun 04, 2010 | Briggs Stratton Portable Generator 305cc...
May 28, 2010 | Briggs & Stratton Electrical Supplies
Nov 29, 2009 | Briggs & Stratton 8,000 Watt 16 Hp...
May 08, 2009 | Electrical Supplies
May 04, 2009 | Briggs & Stratton Power Products 5,550...
May 15, 2017 | Briggs & Stratton Briggs Stratton...
589 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: