Question about Nor-Lake Norlake Refrigeration 4' x 6' Kold Locker Walk-In Cooler - 6' 7'' High w/Floor
Went to start a walk-in cooler after years of down time. The compressor will run for about 10 seconds then shut off for about 30 seconds then run for another 10 & shut off for another 30. Any ideas?
It has lost some freon and is not charged correctly...the unit is pumping down and shutting off on low pressure and then after being off a bit the pressure comes up and it restarts...
Need to check the charge and top it off and you will be good to go..
Posted on May 28, 2010
Testimonial: "Thanx for the good advice."
most likely that walk-in cooler is low on refrigerant (freon). I made video with the same issue. This refrigerator has small leak, i tried to find leak with soap bubbles, but no luck, so end up charging it with freon and add leak dye, so next time I can find that leak for sure.
Posted on Mar 13, 2016
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 10, 2015 | Refrigerators
May 26, 2014 | Dometic Rooftop RV Air Conditioner
Sep 29, 2011 | Heating & Cooling
Aug 13, 2009 | Beverage-Air Kegerator - Beer Keg Cooler...
Sep 16, 2008 | Washing Machines
Jun 22, 2008 | Coleman Mach III Air Conditioner
Mar 31, 2008 | Kenmore 13.7 cu. ft. / 388 liter Upright...
Aug 13, 2007 | Fedders J Chassis A6J12E7A Air Conditioner
236 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: