Question about Honeywell CT3200 5-2 Day Electronic Programmable Thermostat Heater
The air is blowing but it's not cold and the snowflake is still flashing.
Is the AC unit running outdoors? if not , check breakers , and in the electrical disconnect mounted on the wall or unit, there are time delay fuses that can go n
bad. IIf fine with electricity, remove the A/C panel to elec components and depress the contactor to make compressor and fan run, if it does the low voltage(24 volts) isnt making it on yellow and common wire of 24 volt control circuit.
Posted on May 29, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 18, 2017 | Heating & Cooling
May 21, 2017 | Honeywell Heating & Cooling
Aug 02, 2014 | Honeywell Heating & Cooling
May 18, 2013 | 2003 Mitsubishi Eclipse Coupe
Jul 25, 2010 | Haier Heating & Cooling
Jul 20, 2009 | Honeywell Electronic Programmable...
Jan 23, 2009 | Continental CE-AC75271 Ductless Mini Split...
Aug 23, 2008 | 2004 Toyota Camry
Aug 18, 2008 | 2002 Mitsubishi Galant
796 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: