Question about Raypak Free Hydraulic Lift Gate Delivery - No L...
My natural gas raypak pool heater keep clicking to ignite (SPK appears) but won't ignite. The only reading that comes out are CLK and CFH. Read somewhere about cleaning filters and have never done this. this is the 4th season that I've had the heater. thanks
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: "CLK" is being displayed on
CLK stands for Clock. Your heater thinks it is connected to a timeclock and the circuit is open. The connection is on the back of the circuit board, and a communication wire will continue on to your timeclock or controller. Close that circuit and it should fire.
Posted on Sep 28, 2010
you are in fireman switch mode,which means pool timer is ready to shut down pump. clk shuts down heater approx 15 minutes before pump shuts down. this lets heater cool down before pump shuts off.
Posted on Jul 23, 2009
There may be a buildup of carbon on your pilot or your gas pressure may be low. It is hard to say without more info on the heater, gas line size and meter size. Depending on where you live it could also be something like spider webs in your gas orfaces. These will cause all to fire normally but not be consistant enough to read fire back to the ignition control. A small piece of bent wire into the orfaces will help to clear this up. As it is not a heater related problem it will not show a ready made answer on the display. Hope this helps, let me know.
Posted on Nov 07, 2009
Thank you for posting your question here on Fixya.com.
Replacing the roll out switch is an easy do-it-yourself repair. Fixing the problem causing the roll out of the burner flames in the first place is a bit more of a pro job. Something is causing to much heat to roll out the the combustion chamber into the control area causing the switch to fail. You will continue to burn the link until the underlying problem is fixed.
If this answer does not fix your problem, please comment with additional details prior to rating the answer. Positive feedback is appreciated once your problem is solved!
Posted on Jun 01, 2010
Tips for a great answer:
Jul 22, 2014 | Raypak RP2100 DIGITAL POOL HEATER R265
Mar 02, 2013 | Raypak 199500 Btu Digital Natural Gas Pool...
Jun 16, 2012 | Raypak 130,000 BTU Natural Gas Pool...
Jan 17, 2012 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Jan 02, 2012 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Oct 22, 2010 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Sep 28, 2010 | Raypak Free Hydraulic Lift Gate Delivery -...
Aug 16, 2009 | Raypak 130,000 BTU Natural Gas Pool...
345 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: