Question about Ruud UBHC Air Conditioner
While my central air is on, water is leaking from the bottom of the furnace. What is causing this problem?
Any time you have an HVAC problem the best solution is to call a qualified tech. While many problems (and quite possibly this one) aren't that hard to fix the repair cost if you screw something up can be very high. My disclaimer out of the way, here you go:
the condensate (water) is not draining properly. This is either because your pump (if you have one) isn't working, the drain line is clogged (most likely), the gravity drain has been knocked around and feeds back into the furnace, or something more sinister (crack in the evaporator coil pan, for instance). If you have a pump (you'll see PVC running into it and vinyl tubing running out, make sure it's plugged in and the lines are not clogged or kinked. If you have a gravity drain try disconnecting it and blowing it out and making sure it always runs downhill, even if only a little. Other than that, call the HVAC service guys.
Posted on May 26, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 13, 2011 | Heating & Cooling
Jul 12, 2011 | Heating & Cooling
Dec 24, 2010 | Heating & Cooling
Oct 13, 2009 | Goodman Heating & Cooling
Sep 10, 2009 | Weather King 10AJA6001AH Air Conditioner
Aug 20, 2009 | Heil Sound PR-40 Professional Microphone
Aug 02, 2009 | Kenmore Heating & Cooling
Nov 25, 2008 | Heating & Cooling
Oct 05, 2008 | Goodman Heating & Cooling
Sep 01, 2008 | Carrier Heating & Cooling
728 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: