Question about Carrier 38CKC036 Air Conditioner
When desired temperature is reached furnace blower will shut off but compressor will not shut off. only way i can shut it off is with curcit breaker. whats the problem?
Remove the cover on the outside unit that covers the circuit board and contactor and capacitor. Then start the unit and set the thermostat so that the unit cuts off. Then go back to the outside unit and see if the contactor is still pulled in and the unit is running. Next open the breaker and see if the contactor drops out. If it doesn't your contactor could be stuck. Try to free it or replace it. If not the problem could be in the circuit board.
Posted on May 29, 2010
Testimonial: "contacter was welded shut. replaced contacter.working good now."
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 19, 2018 | Heating & Cooling
Dec 26, 2013 | Heating & Cooling
Nov 28, 2012 | Heating & Cooling
Dec 30, 2011 | Heating & Cooling
Aug 30, 2011 | Ruud Heating & Cooling
Aug 18, 2010 | Intertherm Heating & Cooling
Apr 26, 2010 | Heating & Cooling
Jul 03, 2009 | Heating & Cooling
Apr 25, 2009 | Heating & Cooling
Jun 25, 2014 | Carrier 38CKC036 Air Conditioner
Jun 13, 2014 | Carrier 38CKC036 Air Conditioner
438 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: